I have three legs entering with no neutral, from fuses. The voltages on the legs read 120, 208, and 118. When I put a light on the first breaker it will go out within a minute. No matter where I try to hook it up except the high leg the voltage either goes down or up. Is this panel bad or am I doing it wrong?